#114 - What Size Fire Sprinkler Escutcheon Do I Need? Half-Inch vs. Three-Quarter
#114 - What Size Fire Sprinkler Escutcheon Do I Need? Half-Inch vs. Three-Quarter
Mismatched, missing, and damaged “trim plates” could allow fires to spread
The metal fixtures mounted between fire sprinklers and adjacent walls or ceilings may seem like the last thing facilities managers need to worry about. But when they’re damaged or missing – or when the wrong size is allowed to remain in service – fire sprinklers may activate late, allowing a fire to cause unnecessary damage. Those parts, called escutcheons, are specifically engineered for a close fit between the wall or ceiling and the sprinkler. This guide explains why escutcheons matter so much, what size fire sprinkler escutcheon you need, and how you can consistently choose a proper replacement.
Escutcheons enable fire sprinklers to activate quickly
Fire sprinkler escutcheons are called by various names – trim plates, trim rings, wall plates, sleeves, design rings, beauty rings, and extenders, among others. They cover the gap in the wall or ceiling where a fire sprinkler is installed.
Most escutcheons come in recessed, flat, and adjustable styles. Each covers the gap between fire sprinklers and adjacent walls or ceilings, but at different depths. Recessed escutcheons are designed for sprinklers connected to piping behind the wall or ceiling line; flat escutcheons fit sprinklers that are flush; and adjustable escutcheons cover the gap for sprinklers that protrude.
For a complete guide to escutcheon selection, read our article: “Which Fire Sprinkler Escutcheon Do I Need?”
Escutcheons are often confused with fire sprinkler cover plates. But unlike escutcheons, cover plates conceal the sprinkler’s head, providing a degree of tamper and dust-proofing as well as a concealed aesthetic. Cover plates are heat-sensitive, designed with metal components that detach at a rated temperature which is usually about 20 degrees F lower than a sprinkler head’s deployment temperature.
A fire sprinkler cover plate (left) covers the entire sprinkler. The sprinkler head is exposed with an escutcheon (right). Our side-by-side comparison of fire sprinkler covers and escutcheons is available here.
A properly-functioning escutcheon limits airflow into adjacent walls or ceilings. The reason: fire sprinklers are heat-activated, and if heat bypasses a sprinkler, it may not discharge soon enough to effectively control a fire. In addition, escutcheons can impact the deployment of smoke alarms. If smoke escapes through gaps into the ceiling, this could delay an alarm’s detector.
In these situations, seconds count. The Ready Campaign, a Department of Homeland Security disaster-preparedness initiative, estimates that a two-story home may be engulfed in flames just five minutes after ignition begins. Moreover, modern homes (at least the ones without sprinkler systems) are, in some ways, at greater risk than the homes of decades past.
Keith Mulvihill of This Old House, a Connecticut-based home improvement media group, reports that house fires have become more devastating as synthetic materials have become more common. Consumer Safety Director John Drengenberg of Underwriters Laboratory estimates that occupants have only two or three minutes to escape from a home with mostly synthetic-based furnishings – a far cry from the 14 to 17 minutes available decades earlier.
Damaged, altered, or missing escutcheons are an all-too-common fire code failure
Missing escutcheons are surprisingly common. The American Society for Healthcare Engineering reports that a 2014 survey of hospital health and safety compliance identified problems with escutcheons as hospitals’ second-most frequent violation of life safety standards involving fire sprinklers. Massachusetts General Hospital in Boston, MA reiterated the importance of compliance in a 2015 response to their own fire code violations, noting that “[t]hese building features aim to contain smoke and/or fire so that patients may be protected in place or evacuated along a safe route if need be.”
As always, fire code is specifically determined by local and state governments – but these authorities having jurisdiction usually model these standards on code written by the National Fire Protection Association (NFPA). NFPA 25: Standard for the Inspection, Testing, and Maintenance of Water-Based Fire Protection Systems spells out when and how escutcheons should be replaced.
From the 2017 Edition of NFPA 25:
18.104.22.168.1* Any sprinkler that shows signs of any of the following shall be replaced:
(2) Corrosion detrimental to sprinkler performance
(3) Physical damage
(4) Loss of fluid in the glass bulb heat-responsive element
(5) Loading detrimental to sprinkler performance
(6) Paint other than that applied by the sprinkler manufacturer
22.214.171.124.5 Escutcheons and coverplates for recessed, flush, and concealed sprinklers shall be replaced with their listed escutcheon or coverplate if found missing during the inspection.
126.96.36.199.5.1 Where the listed escutcheon or coverplate from a listed assembly is missing and is no longer commercially available, the sprinkler shall be replaced.
188.8.131.52.6 Escutcheons for pendent sprinklers that are not recessed, flush, or concealed shall not be required to be replaced if found missing during the inspection.
In short, missing, damaged, rusted, or painted escutcheons need to be replaced with the same manufacturer’s escutcheon. If a match can’t be located, the entire assembly – both sprinkler head and escutcheon – need to be replaced with a model with comparable characteristics.
For a deeper look at requirements for inspections escutcheons and other fire sprinkler components, read our multi-part series.
When replacing escutcheons, it’s best to look at the sprinkler data sheet Getting the right size is tricky. An escutcheon’s size shouldn’t be taken from any measurement on any part of an escutcheon itself. Measuring the diameter of the escutcheon opening will produce a result that’s too big. And unless you’ve got a spare escutcheon handy, measuring one would require removing it from service – it’s installed with the sprinkler head and can’t be removed without detaching the sprinkler or cutting the escutcheon off entirely.
This is a measurement of the hole in the top of an adjustable escutcheon. It shows that the hole is about ¾” but the escutcheon is really a ½” model. This illustrates how a measurement can give you a general idea of the size you need, but not the actual size.
An escutcheon’s size depends on the K-Factor, or orifice size, of the fire sprinkler’s head. It’s a measurement of the sprinkler’s internal diameter, or the width of the pipe through which water flows. There is a much more straightforward way to determine the size of the escutcheon you need than measurements.
Sprinklers manufactured after December 31st, 2000 have a sprinkler identification number, or SIN. It’s made up of one or two letters followed by three or four numbers – and it provides a straightforward way to determine the exact escutcheon size needed.
To determine your escutcheon size using the SIN:
1) Locate your SIN on the sprinkler’s deflector plate.
3) Enter the four-to-six-character SIN located on the sprinkler’s deflector plate in the Sprinkler Identification Number field. In this case, we’ll start with an example SIN of V2703.
4) The page returns links with the manufacturer’s sprinkler data. Click on the link that’s most appropriate to your location. In the example below, those in the United States should choose the top-most link:
5) Locate the K-factor for your SIN in the tables provided. In this case, each of the sprinklers listed has a K-factor of 5.6:
6) Match your K-Factor to a given escutcheon size using the table below. Often, the K-Factor is either 5.6 or 8.0. Fire sprinkler heads with a 5.6 K-Factor have a ½” orifice and sprinkler heads with an 8.0 K-Factor have a ¾” orifice:
This table lists selected escutcheon sizes for a given K-Factor.
If your sprinklers are really old and don’t have an SIN, you’ll need to find another way to identify the sprinkler’s model and K-Factor – or replace both sprinkler head and escutcheon with a new assembly.
A good rule of thumb: If the sprinkler is older than 2001 and doesn’t have an SIN, it’s going to be ½” the vast majority of the time. This is the size that’s found in most common businesses, with larger escutcheons tending to show up in big manufacturing plants and similar applications.
Also, make sure to understand that replacing a normal escutcheon can require draining a system and taking it out of service, “since the escutcheon opening is smaller than the sprinkler head itself.” To avoid the inconvenience and costs associated with this procedure, “split” escutcheons that are divided into two parts are available, enabling an easier retro-fit. You still have to cut the old escutcheon away, however.
If you need to buy a replacement for a missing, ill-fitting, or damaged fire sprinkler escutcheon, take a look at QRFS’ selection.
And if you still have questions, add a comment below, give us a call at 888.392.3362, or fill out our contact form and we’d be happy to assist.