#379 – Fire Sprinkler Retrofits: An End-User’s Guide to Understanding Systems
#379 – Fire Sprinkler Retrofits: An End-User’s Guide to Understanding Systems
Building owners and managers, residents, and other end-users benefit from learning about a new sprinkler system
Retrofitting an existing building with fire sprinklers is a smart choice that protects lives and property while possibly achieving construction allowances and insurance discounts. And it’s the law, in many cases.
The “model codes” that form the basis of laws have upped the sprinkler requirements for certain occupancies in recent years, including existing high-rises and assembly occupancies. And various states and cities, such as New York City, Florida, San Antonio, Texas, Connecticut, Virginia, New Jersey, and others have enacted various retrofit mandates for specific building types.
Beyond current law, the trend is clear: fire sprinklers save lives—and advocacy groups and lawmakers are pressing for additional mandates in many areas.
Fire sprinkler retrofits are an amazing opportunity to increase public safety. But they also present challenges for some end-users, including knowing when a retrofit is necessary, the logistics of completing one, and developing the knowledge to understand the project and maintain the sprinkler system.
We’ve covered those first two issues (and more) in previous installments of this series:
- Why and When the US Retrofits Sprinklers in Existing Buildings
- Retrofitting Fire Sprinklers: What a Large-Scale Project Needs for Success
Now, we’re going to look at how property owners, managers, and even occupants can get a good understanding of a system as it’s installed and afterward.
Fire sprinkler installation and maintenance rules can be daunting to everyone but the fire sprinkler contractor and design team. But the end-user should still have some knowledge of the equipment that protects them and their property. Let’s dive into some basics.
The standards for sprinklers
Model, local, and state codes outline the rules for when a sprinkler system is required, among many other things. A standard provides the rules for installing and maintaining a fire protection system. Essentially, a code tells “when” something is needed, whereas a standard describes the “how.”
The standard for commercial fire sprinkler installations is NFPA 13: Standard for Installation of Sprinkler Systems. There is also NFPA 13R, which covers low-rise residential structures, and NFPA 13D, which is the home installation standard.
These documents contain the detailed rules for fire sprinkler heads, piping, valves, pipe hangers, spacing, water supply, calculation methods, and a lot more. Code officials—typically fire marshals and inspectors—enforce these rules, which gain the force of law when a model code is adopted as a local or state code.
Engineers and layout technicians design the system using these rules. Fire sprinkler contractors and fitters build it using them.
It starts with the book
NFPA 13 is published by the National Fire Protection Association (NFPA), the leading worldwide authority on fire protection. And it is found in nearly every library, city clerk’s office, building department, and fire department for free public viewing and use.
NFPA also provides a free version to view on its website; simply register for an account and log into your new profile, and a viewable PDF becomes an option.
NFPA 13 is the oldest installation standard in the US. It was first published in 1896 and has been updated nearly every three years since. The latest edition is 2019, but note that most code officials in the country are still using the 2013 or 2016 editions, as there is always a lag in new model codes and standards being adopted as laws.
You can discover which version is being employed in your area by doing an online search, or simply asking your local fire marshal, system designer, or sprinkler contractor.
Who makes these fire sprinkler rules, anyway?
In the first few pages of NFPA 13, there is a summary of the whole 120+ years of the standard, a Table of Contents, and several pages of names.
The latter list shows the members of the technical committees that write the rules in NFPA 13. While the text of the standard may seem dry and complex, remember that each person on the committee is, indeed, a real person!
They are all subject-matter experts in the fire sprinkler field, and each (or, at least, many) can be contacted for more information or questions. Some of them are fire protection equipment manufacturers, others are contractors, and some are code officials. But every member of the NFPA 13 committee is selected and trusted to make the right decision for the minimum—yes, minimum—rules for installing a safe and effective fire sprinkler system.
I have a copy of NFPA 13 and it’s open—now what?
An end-user, such as a condo owner or building manager, is not an expert on fire sprinkler systems—and they are not expected to be! However, it can pay to get to know a system and the rules governing it during and after a fire sprinkler retrofit.
This basic knowledge will help you assess the need (and proposals) for certain design choices and equipment, as well as maintenance down the road. When your contractor calls and tells you that the system needs a hydrostatic test five years from installation, for example, you’ll either know what that is or can find it quickly—and understand why it’s necessary.
And fundamentally, speaking the same language as the designers, installers, and contractors can be a big help, even if it’s not strictly necessary.
If you’re interested in diving into a little “light beach reading,” NFPA 13 is separated into 27 chapters that govern each part of the system. Below are some of the chapters in the 2016 edition—which is still commonly used—where there may be some interest for inquiring minds:
- Chapter 1: Scope, purpose, and application describe the extent of the standard.
- Chapter 3: Definitions that explain the terms used in the standard.
- Chapter 4: General rules for all sprinkler systems. It also requires a document from the owner to the contractor and details requirements for water quality.
- Chapter 6: Allowable materials. Nearly all parts of the sprinkler system are required to be listed, which means they’ve undergone extensive testing for high pressures and durability. Sprinkler systems are NOT plumbing systems. They are subjected to much higher pressures and many components must be able to withstand higher temperatures, for example.
- Chapter 7 describes all of the system types— wet, dry, preaction, etc. Chances are, the system in your retrofitted building is water-filled, or commonly referred to as a “wet-pipe system.” Regardless, this chapter covers all of the types.
- Chapter 8: Sprinkler uses, spacing, positioning, obstruction rules, and more.
- Chapter 9: How to support the sprinkler system. For example, it goes over the rules for hangers that support the pipe and bracing for earthquake-prone areas.
- Chapter 11 answers questions on how much water will flow.
- Chapter 23: It has all of the rules for what is required on the construction plans (commonly referred to as “shop drawings”) and how to hydraulically calculate the system’s water flow and pressure demands. The latter is a complex topic, so be prepared to nerd out.
- Chapter 27: An introduction to the rules for maintaining the fire sprinkler system once it’s installed. This leads to an entirely new standard of mandatory rules: NFPA 25: Standard for the Inspection, Testing, and Maintenance of Water-Based Fire Protection Systems. This document is available in all of the places where NFPA 13 is found, including an online version at the NFPA website. But a building owner/manager should have an onsite copy of this document, too!
The above list covers the order of these chapters for the 2016 edition of NFPA 13. Though it has not been adopted everywhere yet, some jurisdictions and fire protection professionals are using the 2019 version.
Most of the information in the newer standard remains the same, but the book was reorganized to cover the topics in sequential order during a system installation. To learn more about these differences, check out our previous blogs:
- Significant Changes to the 2019 Edition of NFPA 13, Part 1
- Significant Changes to the 2019 Edition of NFPA 13, Part 2
I spy, with my little eye—stuff you can see on a fire sprinkler system after a retrofit
Much of the sprinkler system is buried behind walls or in control rooms (commonly called “riser rooms”). However, there are parts of the set-up, such as those in the stairwells, corridors, offices, or residences, that are seen every day. And facility managers can even visually inspect some of these components.
Stairways—fire sprinkler piping
Most stairways will have fire sprinkler and standpipe piping in it. Standpipes are often found in combination with sprinklers in buildings of a certain size that require them; they serve as a sort of internal network of fire hydrants that firefighters can access via hoses.
These pipes are usually vertical black steel or orange plastic (CPVC) lines, with some horizontal parts. Many times, the vertical piping is in a corner of the floor landing with a large outlet and handle—that is the “standpipe hose valve” that’s used by the fire department when they respond to a fire. Just like fire trucks connect to hydrants on the street, a standpipe hose valve on each floor is the firefighter's hydrant.
Near the ceiling of each floor landing, it is common to see a section that has piping, a pressure gauge, a control valve, a drain, and a waterflow switch. This is called the “floor control assembly.” It serves as the shut-off to the fire sprinkler system on that floor. Every floor should have one.
The control valve can be supervised by a fire alarm panel—if someone shuts the valve, the fire department is notified. Some valves have a chain and lock, so they cannot be physically shut.
Corridors, public spaces, and dwelling units
The most identifiable parts and workhorses of the system are the individual fire sprinklers. Fire sprinkler heads are usually located in the ceiling (pendent) or on the wall (sidewall) near the ceiling. Some fire sprinklers are exposed—the frame, bulb, and deflector are visible. Others are visible only by spotting a flat, round plate. These are called “concealed sprinklers” and all of the operating parts are behind the “cover plate.”
Sprinklers come in many different colors and finishes, but it is important not to paint or caulk when remodeling or changing the colors in a dwelling unit. Additional layers of paint or caulk can delay or prevent sprinklers from operating during a fire.
Sprinklers are spaced apart from each other based on the rules in NFPA 13. For example, the amount of water pressure and the size of the sprinkler’s orifice can change the spacing of sprinklers. Generally, the higher the pressure, the fewer sprinklers installed.
Sprinklers in a corridor have a typical spacing of 12–20 feet apart. Inside a dwelling unit, at least one sprinkler is in each occupied room, such as kitchens, living rooms, and bedrooms. Small bathrooms and closets may not have a sprinkler, as model code does not require them in specific installations—though some state laws may.
Sprinklers inside a dwelling unit typically cover from 130–400 square feet per sprinkler and the larger room, the more sprinklers. The same goes for the other public spaces within the building. A library, salon, recreation, or exercise room will have similar spacing rules.
A little end-user knowledge goes a long way in a fire sprinkler retrofit
Qualified contractors and professional designers retrofit buildings with fire sprinkler systems. But each construction trade person and facility manager should take the time to educate end-users during the process, on each phase of installation. A basic level of knowledge helps owners, managers, and even residents maintain the system, know how it works, and have confidence that it will protect people and property during an emergency.
And regardless of the law governing retrofits for a specific building—or the age of the building and its use—fire sprinklers are a worthwhile investment. As the National Fire Sprinkler Association (NFSA) puts it, “Fire sprinklers buy time. Time buys life.”
If you have complex questions about the application of a system, a specific project, or how to interpret codes and standards, use QRFS’s Ask a Fire Pro service. A highly-qualified fire protection professional will get you an answer in three business days!
Questions? Call us at +1 (888) 361-6662 or email [email protected].