#40 - Quick Response Sprinkler: The Definitive Guide
#40 - Quick Response Sprinkler: The Definitive Guide
All quick response fire sprinkler heads prioritize human survival
Residential buildings, hospitals, offices, and buildings of various kinds often combine few escape routes with an abundance of people—a dangerous pairing in a fire emergency. To give people in those buildings a better shot at survival, fire sprinkler manufacturers developed the quick-response sprinkler, designed first and foremost to help people escape burning buildings before it's too late.
In this article, we explain the mission of a quick response fire sprinkler head and provide an overview of quick response sprinkler types, characteristics, and identification to help consumers find exactly the head they're looking for.
If you'd prefer, you can skip straight to our selection of quick response fire sprinklers.
Quick response fire sprinklers delay the most deadly fire scenarios
Fire sprinklers suppress fires by soaking ignitable material near the flames. In doing so, they make it harder for a fire to spread, buying valuable time for the fire department to arrive. But the spray pattern of quick response fire sprinkler heads—and the design of the systems supplying them with water—emphasize covering nearby walls with lots of water.
Soaking the walls serves two purposes. First, fire rises and most modern buildings feature an abundance of thin walls. Keeping the walls moist slows the fire's natural upward progression. Second, as fire burns, it emits carbon monoxide (CO) and other gasses that are flammable in the right concentrations. Since CO is slightly lighter than air, it rises with heat currents and accumulates near the ceiling. Keeping the fire contained to the floor keeps the ceiling temperatures (and all the CO it produces) cooler.
Why is that important? Flashover starts when the accumulated carbon monoxide and other gases near the ceiling combust—somewhere around 900 to 1,200 degrees Fahrenheit—setting off a chain reaction that ends with all the oxygen incinerated. Anyone left inside the room dies almost instantly. For a dramatic demonstration of the devastating power of flashover, take a look at the video below:
In short, avoiding flashover is necessary to human survival, and cooler ceiling temperatures help tremendously. Quick response sprinkler system design accomplishes this mission through proper spacing, early activation, and specialized spray patterns. Tests have shown that quick-response sprinklers can lower temperatures 400 degrees Fahrenheit over standard-response sprinklers, keeping temperatures well away from flashover.
Sprinkler style or orientation limits appropriate uses and coverage characteristics
Quick response fire sprinkler heads are available in many different styles, temperatures, and colors. While various styles are available, the four most common styles for quick response sprinklers include:
• Pendent: hangs down from piping with the head exposed
• Concealed pendent: installs in ceilings with the head hidden from view
• Upright: often used with exposed piping, these heads point upward to spray around obstructions
• Horizontal sidewall: mounts to piping behind a wall with the head parallel to the ground
Each of these styles is better suited to some applications rather than others. As we've covered in our in-depth look at fire sprinkler head types, pendent sprinklers protrude from the ceiling, leaving the frame visible. There are some exceptions: flush pendent sprinklers keep the working parts (like the deflector, frame, and bulb) out of sight. Concealed sprinklers also keep important parts out of sight but do so using decorative cover plates in a variety of finishes.
Unlike pendent sprinklers, upright sprinkler heads are used in locations where obstructions interfere with sprinkler coverage or where freezing temperatures threaten to damage sprinkler heads. Similarly, sidewall sprinkler heads are often installed when obstructions or aesthetic concerns weight against the use of other sprinkler types. Most often, these sprinklers protect hallways, closets, or other limited areas.
Quick response fire sprinkler heads are available in a variety of temperatures and finishes
In turn, any one of these sprinkler types is available in a variety of temperatures. The temperature at which a quick response fire sprinkler head activates depends on building usage, ambient temperature, the presence of nearby heat sources, and location. The most common temperature is 155 degrees Fahrenheit, but 200 and 286 degrees are also prevalent.
Pendent, upright, and horizontal sidewall sprinklers are available in a variety of finishes, with the three most common being brass, chrome, and white. Many manufacturers also offer special corrosion-resistant finishes for humid, outdoor, or coastal environments where ambient moisture quickly degrades metal. Finally, where sprinklers include cover plates, a variety of finishes are available, ranging from the simple colors discussed above to wood-patterned finishes and even custom colors made to match existing ceilings.
Some basic tips can help consumers identify which quick response fire sprinkler head they already have
Many fire sprinklers feature temperature-sensitive bulbs. While the color of that bulb indicates how hot the surrounding air must be for the fire sprinkler to activate, the bulb's diameter indicates whether or not it's a quick response fire sprinkler.
The size of the bulb is usually the easiest way to compare quick response and standard response sprinklers. As pictured below, thicker five-millimeter (5 mm) bulbs are standard response sprinkler heads. Quick response fire sprinklers feature lean three-millimeter (3 mm) bulbs.
There are some exceptions to this rule, though. Not all quick-response fire sprinkler heads feature bulbs. Some use heat-sensitive metal parts, or fusible links, that respond to heat in much the same way that these bulbs do.
To find an appropriate match, it's critical to inspect the sprinkler's deflector plate. Manufacturers will typically stamp QR (Q.R.) or SR (S.R.) on the deflector’s spindles. It's also a good idea to find the sprinkler's model number and enter it in a search engine just to be sure. That model number consists of four to six letters and numbers, beginning with one or two letters to indicate the manufacturer, where TY for Tyco, V for Victaulic, and so on.
QRFS makes it easy to find the quick response sprinkler you need
Now that you've got a handle on the basics of quick response fire sprinklers. check out QRFS's selection of quick response pendents, concealed pendents, uprights, and sidewalls from Victaulic, Tyco, Senju and more in a variety of temperatures and finishes.
These UL-listed and FM-approved fire sprinklers comply with standards for NFPA fire sprinkler systems, including commercial (NFPA 13), residential (NFPA 13R), and home fire sprinkler systems (NFPA 13D).
Questions? Need some help identifying or replacing your quick response sprinkler? Call us at (888) 361-6662 or email [email protected].
This blog was originally posted by Jason Hugo at QRFS.com/blog on March 6, 2016, and updated on April 28, 2019. If this article helped you find the sprinkler you needed, check us out at Facebook.com/QuickResponseFireSupply or on Twitter @QuickResponseFS.