Viking Fire Sprinkler 5.6K Chrome Horizontal Sidewall QR 155F | VK305
- Buy 10 for $12.30 each and save 5%
- Buy 50 for $11.66 each and save 10%
- Buy 100 for $11.01 each and save 15%
|VK305CH155||Brass Frame And Copper Deflector||1/2" (12.7 mm) NPT||5.6K|
|Temperature Rating||Maximum Working Pressure||Availability|
|155F (68C)||175 PSI (12.1 BAR)||Usually ships within 48 hours|
Viking Microfast Quick Response Chrome Horizontal Sidewall Fire Sprinkler delivers powerful, affordable fire suppression in ordinary hazard commercial occupancies such as universities, auditoriums, churches, and parking garages. Using a heat-activated 3mm glass bulb, this automatic fire sprinkler opens when ambient temperatures reach 155F (68C), reducing the likelihood of flashover and facilitating safe evacuation.
The Viking Model Microfast has a 5.6 K-Factor and installs with 1/2" (12.7 mm) National Pipe Thread (NPT), used in fire sprinkler systems throughout the United States. This Quick Response Fire Sprinkler features a brass frame, copper deflector, and a nickel-alloy spring sealing assembly with PFTE tape.
This 155F (68C) temperature rating strikes a balance between a fire sprinkler that activates too soon, causing accidental discharge, and too late. 155F (68C) Quick Response Fire Sprinklers can be installed to wet and dry pipe fire sprinkler systems, and are preferred for use in one and two-family dwellings, apartments, duplexes, and boarding houses. The Viking Microfast is also a suitable choice for installation in many college dormitories, condominiums, and nursing homes.
With a maximum working pressure of 175 PSI (12.1 BAR), this horizontal sidewall sprinkler installs on a wall or the side of a beam where ceiling piping is not desirable and may be installed and used in accordance with NFPA 13 and local fire code. Each Model Microfast sprinkler is made by Viking, a global leader in fire protection manufacturing for nearly 100 years.
This product is UL & FM approved, and appropriate for use in fire protection systems when accepted by the authority having jurisdiction. In accordance with NFPA 13, a higher temperature rating may be required when installing a quick response fire sprinkler in or near heat sources, unventilated spaces, uncovered steam mains, or uninsulated rooftops.