Viking Fire Sprinkler 5.6K White Pendent QR 155F | VK302
- Buy 50 for $11.11 each and save 7%
- Buy 100 for $10.52 each and save 12%
- Buy 500 for $9.92 each and save 17%
|VK302WH155||White Finish, Brass Frame, And Copper Deflector||1/2" (12.7 mm) NPT||5.6K|
|Temperature Rating||Maximum Working Pressure||Approvals and Listings||Availability|
|155F (68C)||175 PSI (12.1 BAR)||cULus, FM, VdS, LPCB, CE, CCCF, MED||In Stock|
Viking Microfast VK302 Quick Response White Pendent Fire Sprinkler delivers powerful, affordable fire suppression in ordinary hazard commercial occupancies such as universities, auditoriums, churches, and parking garages. Using a heat-activated 3mm glass bulb, this automatic fire sprinkler opens when ambient temperatures reach 155F (68C), supporting rescue and evacuation efforts by lowering ambient temperatures.
The Viking Microfast VK302 has a 5.6 K-Factor and installs with 1/2" (12.7 mm) National Pipe Thread (NPT), used in fire sprinkler systems throughout the United States. This Quick Response Fire Sprinkler features a white finish, brass frame, brass screw, copper deflector, and a spring sealing assembly made with nickel alloy and PTFE tape.
With a discharge temperature of 155F (68C), these sprinklers activate early enough to provide robust protection to people and property while reducing the risk of accidental discharge. 155F (68C) Quick Response Fire Sprinklers are preferred for use in cafeterias, auditoriums, convention centers and other gathering spaces where human safety is the first priority. The Viking Microfast VK302 is a multi-purpose head suitable for use in covered horse stables, canneries, and many industrial applications.
With a maximum working pressure of 175 PSI (12.1 BAR), this pendent sprinkler hangs from above-ceiling piping and may be installed and used in accordance with NFPA 13 and local fire code. Each Microfast VK302 sprinkler is made by Viking, a global leader in fire protection manufacturing for nearly 100 years.
This product is UL & FM approved for use in fire protection systems when accepted by the authority having jurisdiction. In accordance with NFPA 13, a higher temperature rating may be required when installing a quick response fire sprinkler in or near heat sources, unventilated spaces, uncovered steam mains, or uninsulated rooftops.