Viking Fire Sprinkler 8.0K Brass Upright SR 155F | VK200
- Buy 50 for $14.83 each and save 7%
- Buy 100 for $14.04 each and save 12%
- Buy 500 for $13.24 each and save 17%
|VK200BR155||Brass Finish, Brass Frame, And Copper Deflector||1/2" (12.7 mm) NPT||8.0K|
|Temperature Rating||Maximum Working Pressure||Approvals and Listings||Availability|
|155F (68C)||175 PSI (12.1 BAR)||cULus, FM, VdS, LPCB, CE, CCCF, MED||In Stock|
Viking VK200 Standard Response Brass Upright Fire Sprinkler delivers powerful, affordable fire suppression in ordinary hazard commercial occupancies such as universities, auditoriums, churches, and parking garages. Using a heat-activated 5mm glass bulb, this automatic fire sprinkler opens when ambient temperatures reach 155F (68C), drenching the area surrounding a fire to keep it in its place of origin.
The Viking Model VK200 has a 8.0 K-Factor and installs with 1/2" (12.7 mm) National Pipe Thread (NPT), used in fire sprinkler systems throughout the United States. This Standard Response Fire Sprinkler features a brass finish, brass frame, brass screw, copper deflector, and a spring sealing assembly made with nickel alloy and PTFE tape.
With a discharge temperature of 155F (68C), these sprinklers activate early enough to provide robust protection to people and property while reducing the risk of accidental discharge. 155F (68C) Standard Response Fire Sprinklers are preferred for use in cafeterias, auditoriums, convention centers and other gathering spaces where human safety is the first priority. The Viking Model VK200 is a multi-purpose head suitable for use in covered horse stables, canneries, and many industrial applications.
With a maximum working pressure of 175 PSI (12.1 BAR), this upright sprinkler limits debris and ice buildup by installing vertically and may be installed and used in accordance with NFPA 13 and local fire code. Each Model VK200 sprinkler is made by Viking, a global leader in fire protection manufacturing for nearly 100 years.
This product is UL & FM approved for use in fire protection systems when accepted by the authority having jurisdiction. In accordance with NFPA 13, a higher temperature rating may be required when installing a standard response fire sprinkler in or near heat sources, unventilated spaces, uncovered steam mains, or uninsulated rooftops.