Viking Residential Fire Sprinkler 4.2K White Horizontal Sidewall 155F | VK484
- Buy 50 for $10.18 each and save 7%
- Buy 100 for $9.64 each and save 12%
- Buy 500 for $9.09 each and save 17%
|VK484WH155||White Finish, Brass Frame, And Brass Deflector||1/2" (12.7 mm) NPT||4.2K|
|Temperature Rating||Maximum Working Pressure||Approvals and Listings||Availability|
|155F (68C)||155 PSI (10.7 BAR)||cULus, NYC||Usually ships within 48 hours|
Viking VK484 Residential Fast Response White Horizontal Sidewall Fire Sprinkler delivers powerful, affordable fire suppression in ordinary hazard residential occupancies such as homes, apartments, dormitories, and hotels. Using a heat-activated 3mm glass bulb, this automatic fire sprinkler opens when ambient temperatures reach 155F (68C), supporting rescue and evacuation efforts by lowering ambient temperatures. Designed for residential applications, the 4.2K orifice makes efficient use of available water supplies in smaller sprinkler systems.
Viking's Freedom Residential Pendent Sprinklers are designed to be unobtrusive, fast-acting, and capable of providing coverage of up to 16 feet by 20 feet (4.9 m x 6.1 m). Designed for residential applications, the 4.2K orifice makes efficient use of available water supplies in smaller sprinkler systems.
The Viking Model VK484 has a 4.2 K-Factor and installs with 1/2" (12.7 mm) National Pipe Thread (NPT), used in fire sprinkler systems throughout the United States. This Residential Fast Response Fire Sprinkler features a white finish, brass frame, brass screw, brass deflector, and a spring sealing assembly made with nickel alloy and PTFE tape.
With a maximum working pressure of 155 PSI (10.7 BAR), this horizontal sidewall sprinkler installs on a wall or the side of a beam where ceiling piping is not desirable and may be installed and used in accordance with NFPA 13, NFPA 13R, NFPA 13D and local fire code. Each Model VK484 sprinkler is made by Viking, a global leader in fire protection manufacturing for nearly 100 years.
This product is UL-listed, and appropriate for use in fire protection systems when accepted by the authority having jurisdiction. In accordance with NFPA 13, a higher temperature rating may be required when installing a residential fast response fire sprinkler in or near heat sources, unventilated spaces, uncovered steam mains, or uninsulated rooftops.