Senju 140F (60C) White Square Cover Plate for RC Heads | 2 5/8" (66.68 mm)
- Buy 10 for $12.30 each and save 5%
- Buy 100 for $11.01 each and save 15%
- Buy 500 for $9.07 each and save 30%
|SKU||Senju Part Number||Cover Plate Temperature||Finish|
|Fire Sprinkler Temperature||Fire Sprinkler Models||Approvals / Listings||Availability|
|162F (72C) to 175F (79C) Fire Sprinklers||For Senju Model RC-QR, RC-RES, & RC-QR-EC Fire Sprinklers (See SINs Below)||cULus, FM, and/or other organizations depending on the sprinkler||In Stock|
White 140F (60C) Cover Plate Assembly for Senju RC-QR, RC-RES, & RC-QR-EC Fire Sprinklers activates at 140F (60C) to facilitate timely activation of fire sprinkler heads with temperatures rated at 162F (72C) to 175F (79C).
Sprinkler Identification Numbers (SIN) for this White 140F (60C) Cover Plate Assembly for Senju RC-QR, RC-RES, & RC-QR-EC Fire Sprinklers include:
This White 140F (60C) Cover Plate Assembly for Senju RC-QR, RC-RES, & RC-QR-EC Fire Sprinklers is listed by cULus, FM, and/or other organizations depending on the sprinkler. When this white fire sprinkler cover plate reaches a specified temperature the solder holding the plate's decorative exterior on the frame melts, and the two separate. Cover plates in stock finishes other than white are available on our site, and custom-finished may be available by special order - call us at 888-361-6662 or click here to contact us.
For many cover plates, the rated temperature is at least 20F (6.7C) cooler than the sprinkler head's activation temperature, which ensures that the cover plate detaches early enough to allow the sprinkler to activate on time. However, each manufacturer's product line varies slightly and cover plate temperatures may be closer to or further away from the fire sprinkler's activation temperature. Use only the cover plate approved by the manufacturer for your specific sprinkler.
Fire Sprinkler Helpful Tips:
Tip 1: When replacing cover plates it is important to purchase replacements from the same manufacturer as the fire sprinkler. Each manufacturer's plate is a little different in size, color, and so on. The manufacturer and temperature of a cover plate is printed on the base of the plate. To view this information, remove the cover plate. Most cover plates are either twist off or pull off.
Tip 2: Any modifications or replacements to a fire sprinkler system should be performed by qualified professionals.
Tip 3: National Fire Protection Association (NFPA) guidelines state that spare fire sprinkler heads and a wrench should be accessible at all times in a facility with a commercial fire sprinkler system installed. Often, state regulations also apply. Check with your local fire department.
Tip 4: All fire sprinkler systems should be visually inspected (often) and professionally inspected (annually).