Viking Fire Sprinkler 5.6K Concealed Pendent QR 155F | VK462 | 13503A
- Buy 50 for $27.85 each and save 7%
- Buy 100 for $26.36 each and save 12%
- Buy 500 for $24.86 each and save 17%
|VK462CP155||Brass Body And Copper Deflector||1/2" (12.7 mm) NPT||5.6K|
|Temperature Rating||Maximum Working Pressure||Approvals and Listings||Cover Plate Activation Temperature|
|155F (68C)||175 PSI (12.1 BAR)||cULus, VdS, FM, LPCB, CE, NYC||135F|
|Cover Plate Finishes||Availability|
|White, Black, and Chrome in 2 3/4" or 3 5/16" Sizes - Cleanroom Seal Available||Usually ships within 48 hours|
Viking Mirage Quick Response Concealed Pendent Fire Sprinkler delivers decorative, competitively-priced defense against fire in ordinary hazard commercial occupancies such as universities, auditoriums, churches, and parking garages. Using a heat-activated 3mm glass bulb, this automatic fire sprinkler opens when ambient temperatures reach 155F (68C), reducing the likelihood of flashover and facilitating safe evacuation.
The Viking Model Mirage has a 5.6 K-Factor and installs with 1/2" (12.7 mm) National Pipe Thread (NPT), used in fire sprinkler systems throughout the United States. This Quick Response Fire Sprinkler features a brass body, copper deflector, and nickel-alloy sealing assembly with PFTE tape.
This 155F (68C) temperature rating strikes a balance between a fire sprinkler that activates too soon, causing accidental discharge, and too late. 155F (68C) Quick Response Fire Sprinklers can be installed to wet and dry pipe fire sprinkler systems, and are preferred for use in one and two-family dwellings, apartments, duplexes, and boarding houses. The Viking Mirage is also a suitable choice for installation in many college dormitories, condominiums, and nursing homes.
With a maximum working pressure of 175 PSI (12.1 BAR), this pendent sprinkler hangs from above-ceiling piping and may be installed and used in accordance with NFPA 13 and local fire code. Each Model Mirage sprinkler is made by Viking, a global leader in fire protection manufacturing for nearly 100 years.
This product is UL & FM approved, and appropriate for use in fire protection systems when accepted by the authority having jurisdiction. In accordance with NFPA 13, a higher temperature rating may be required when installing a quick response fire sprinkler in or near heat sources, unventilated spaces, uncovered steam mains, or uninsulated rooftops. Concealed pendent sprinklers should not be installed where the air pressure above the ceiling is greater than the pressure below, which may prevent or delay sprinkler activation in the event of a fire.