Victaulic domed cover plate for fire sprinkler model V2734, V2726, V3904, and V2742. When a cover plate reaches a specified temperature the solder holding the decorative exterior of the cover plate to its frame melts and the two separate. The temperature of the cover plate should be at a minimum 20ï¾°F cooler than the sprinkler head itself ensuring adequate separation time prior to sprinkler activation.
Not the fire sprinkler cover plate you're looking for? See all sprinkler covers.
Fire sprinkler cover plate is available online in two temperatures:
135° F, 57° C & 155° F, 68° C
Fire sprinkler concealer plate available online in three finishes:
Chrome Plated, White Painted
*Black and other colors available by special request. All special request domed cover plates, including chrome, are special order and are non-refundable, non-returnable.
Fire sprinkler cover plate listings:
UL Listed, ULc Listed, FM Approved
Can I paint my fire sprinkler cover plate?
Fire Sprinkler Helpful Tips:
Tip 1: When replacing coverplates it is important to purchase replacements from the same manufacturer as the fire sprinkler. Each manufacturer's plate is a little different in size, color, etc. Manufacturer and temperature of a coverplate is printed on the base of the plate requiring removal to inspect. Most cover plates are either twist off or pull off.
Tip 2: It is recommended that a qualified professional replace fire sprinklers or in any other way modify a fire sprinkler system.
Tip 3: Spare fire sprinkler heads and a wrench should be accessible at all times in a facility with a commercial fire sprinkler system installed. Often state regulations apply, too. Check with your local fire department.
Tip 4: Fire sprinkler systems should be visually inspected often and professionally inspected annually.