Tyco Fire Sprinkler 5.6K White Pendent SR 155F | TY325
- Buy 50 for $8.32 each and save 7%
- Buy 100 for $7.88 each and save 12%
- Buy 500 for $7.43 each and save 17%
|TY325WH155||White Finish, Bronze Frame, And Bronze Deflector||1/2" (12.7 mm) NPT||5.6K|
|Temperature Rating||Maximum Working Pressure||Approvals and Listings||Availability|
|155F (68C)||175 PSI (12.1 BAR)||UL, ULC, FM, LPCB, VdS, CE||In Stock|
Tyco TY325 Standard Response White Pendent Fire Sprinkler delivers dependable, competitively-priced protection against fire in light and ordinary hazard commercial occupancies such as universities, auditoriums, churches, and parking garages. Using a heat-activated 5mm glass bulb, this automatic fire sprinkler opens when ambient temperatures reach 155F (68C), drenching the area surrounding a fire to keep it in its place of origin.
The Tyco Model TY325 has a 5.6 K-Factor and installs with 1/2" (12.7 mm) National Pipe Thread (NPT), used in fire sprinkler systems throughout the United States. This Standard Response Fire Sprinkler features a white finish, bronze frame, bronze compression screw, bronze deflector, and a stainless-steel seating assembly with Teflon.
This 155F (68C) temperature rating strikes a balance between a fire sprinkler that activates too soon, causing accidental discharge, and too late. 155F (68C) Standard Response Fire Sprinklers are preferred for use in theaters, restaurants, and other gathering spaces where human safety is the first priority. The Tyco Model TY325 is also perfect for use in animal shelters, agricultural and food processing facilities, and fairgrounds.
With a maximum working pressure of 175 PSI (12.1 BAR), this pendent sprinkler hangs from above-ceiling piping and may be installed and used in accordance with NFPA 13 and local fire code. Each Model TY325 sprinkler is made by Tyco, a global manufacturer with more than a half-century in the fire protection industry.
This product is UL & FM approved for use in fire protection systems when accepted by the authority having jurisdiction. In accordance with NFPA 13, a higher temperature rating may be required when installing astandard response fire sprinkler in or near heat sources, unventilated spaces, uncovered steam mains, or uninsulated rooftops.